Analysis on High and Low Voltage Fault Detection and Solving Method of Scroll Chiller in Summer
1, Scroll Chiller fault detection: the high and low pressure are higher than usual normal pressure
Failure Analysis: This is due to the presence of air or refrigerant in the system. Or is poor heat dissipation, especially when the ambient temperature is relatively high. Solution: the former need to re-vacuum this time, then add the right amount of refrigerant will be able to solve the problem. The latter will try the condenser heat sink cleaning.
2, Scroll Chiller fault detection: high and low pressure than usual normal pressure is low
Failure Analysis: This may be caused by the refrigeration system blockage, blocking parts of the throttle, throttle parts will be a significant temperature difference, feel the hand can find the problem. Solution: At this time must use the Scroll Chiller detector to identify the leaked parts, for repair.
3, Scroll Chiller fault detection: high pressure is low, and low pressure and high, the rolling cold water machine cooling can never achieve the normal effect.
Failure Analysis: The reason is likely to be Scroll Chillers pump wear, resulting in power drop. Solution: Then you need to replace the compressor. 4, when the Scroll Chiller work, the pressure gauge jitter, indicating that the system has moisture. Solution: At this time need to re-vacuum, pumping time not less than a quarter of an hour, if necessary, the best change for the dry filter to completely rule out the water in the cooling system.
At present, China's Scroll Chiller, ice machine market, in addition to Scroll Chillers, ice water machine, the majority of environmentally friendly energy-saving Scroll Chiller, ice machine, with the technology constantly updated and improved, so large Some customers on the Scroll Chiller, ice water machine products have a deeper understanding. In recent years in the plastics industry, packaging industry, mold industry, and plastic associated with the Scroll Chiller, ice machine can be seen everywhere. Therefore, the Scroll Chiller, ice machine in a number of areas has long been an indispensable peripheral machinery and equipment.
However, the Scroll Chiller, ice machine, mold temperature production enterprises most need to pay attention to is that plastic Scroll Chiller, ice machine, mold temperature machine in recent years in the food industry is widely used, food safety issues already Rose to the national level. Therefore, in the field of food used in plastic Scroll Chiller, ice machine, mold temperature machine products must be strict quality, enterprises to avoid unqualified products into the food industry, resulting in food safety incidents, for enterprises and industries to bring losses and negative Influence, only in product quality and safety to do bit, enterprises can get more economic benefits.
From the entire Scroll Chiller, ice machine industry point of view, the development of the status quo is relatively optimistic, the industry's achievements worthy of recognition. The future of plastic Scroll Chiller, ice water machine products there is a great market development space. Plastic Scroll Chiller, ice machine in the export also maintained a good growth trend, the future also requires enterprises to adapt to market changes, and constantly improve the production equipment, continue to improve product quality, produce more stable performance, wider application, More cost-effective products.
In the continuous development of the market today, plastic Scroll Chiller, ice machine industry, although there is a vast market development space, but with the market demand for packaging products is getting higher and higher, plastic Scroll Chiller, ice machine industry in the The future development will encounter many problems, can do timely response, an effective solution to the problems in the development, is the test of China's plastic Scroll Chiller, ice machine industry is really an important sign of maturity.