As we all know, small industrial water chillers refer to water chillers with small power or small volume. When the auxiliary equipment cools down, the small water chillers can be moved freely according to the cooling needs. Small industrial water chillers are cooling equipment that can provide constant temperature, constant current and constant pressure. A certain amount of water is injected into the internal water tank of the machine, and the water is cooled by the cooling system of the water chillers. Then a water pump inside the machine injects the low-temperature frozen water into the equipment to be cooled. The frozen water takes away the heat inside the machine, and the high-temperature hot water is returned to the water tank again to cool down. Thus, the circulation exchange cooling achieves the effect of cooling the equipment. Do you know how to prolong the service life of small industrial chillers?
Methods for prolonging service life of small industrial chillers;
1. Keep the small industrial water chillers clean and well ventilated. Clean the condenser regularly to ensure the normal operation of the small industrial water chillers.
2. The settings of various protection devices for small industrial water chillers have been set by the water chillers manufacturer. Users are not allowed to change them at will.
3. Chillers shall maintain the quality of water quality to prevent impurities in water from entering small industrial chillers and causing blockage.
4. If the small industrial water chiller is stopped for a long time in winter, the small industrial water chiller shall be turned off first, then the main power supply shall be turned off, and the water in the water chiller shall be drained completely.
5. When the small industrial water chiller is stopped due to a fault alarm, the alarm stop button shall be pressed first, and then the cause of the fault shall be checked. It is not allowed to forcibly start the operation before the fault is eliminated.
6. To ensure good heat dissipation effect, it is necessary to keep the surface of the heat dissipation coil of the small industrial water chiller clean, ensure the air circulation around the machine and low temperature, and regularly clean the heat dissipation coil.