About Industrial Chiller
Icing in the circulating water tank
1.Insufficient cooling The lack of refrigerant or pipeline leakage, Supplementary refrigerant or welding after leak detection, Evacuation of the refrigerant and supplement of the cooling medium, Radiator is too dirty, The radiator valve is not opened or opened too small, The radiator is cleaned and the valve is fully opened.
2. The set temperature is over, and the low correction value is set.
3. The water in the water tank has no circulating water, and a circulating water circuit is shorted between the frozen water outlet and the inlet.
4.Temperature control Table out of control, replace the temperature control table High-voltage fault Heat dissipation is not good, the radiator is dirty, cleaning the radiator can not be good wind, improve the ventilation conditions.
The cooling fan does not work, check the fan motor is burned out short circuit repair or replace the motor motor high pressure engine damage, replace High pressure engine six, according to the table temperature shows the number of up and down beating 1. The temperature line and temperature measuring body are dirty, the temperature measuring body is wiped clean 2. The temperature control table is damaged, repair or replace the temperature control table 3. The temperature line is bad , repair or replace the temperature line .