In the refrigeration industry, it is divided into two types: air-cooled chillers and water-cooled chillers. According to the compressor, it is divided into screw chillers, scroll chillers, and centrifugal chillers.
In terms of temperature control, it is divided into low temperature industrial chillers and normal temperature chillers. The temperature of normal temperature units is generally controlled within the range of 0 degrees to 35 degrees. Low temperature unit temperature control is generally around 0 degrees to -100 degrees.
Chillers are also known as: chillers, refrigeration units, ice chillers, cooling equipment, etc. Because of the wide range of uses in various industries, the requirements for chillers are also different. Its working principle is a multifunctional machine that removes liquid vapor through compression or heat absorption refrigeration cycles.
Electroplated Water Cooling Chiller Manufacturers
|Standard compressor||Pansonic scroll type|
|Rated cooling capacity||49.9KW/14.2Ton/42948Kcal/H|
|Condenser||Shell and tube kind|
|Evaporator||Stainless steel water tank type/ 148L|
|Water flow in Condenser||10.31m3/h|
|Standard chilled water flow||8.59M3/H|
|Diameter of pipe||DN40 mm|
|Machine size||1200*700*1200 mm|
Electroplated Water Cooling Chiller More Pictures For Refrence
Production Flow For Reference
Water chiller is a kind of water cooling equipment, which can provide constant temperature, constant current and constant pressure cooling equipment. The principle of the chiller is to inject a certain amount of water into the internal water tank of the machine, and the water is cooled by the chiller refrigeration system, and then the internal water pump injects low-temperature frozen water into the equipment that needs to be cooled, and the chilled water will heat the internal heat of the machine. Take it away and return the high-temperature hot water to the water tank to cool down again. In this way, it is cyclically exchanged and cooled to cool the equipment.